RCD Fault Finding
Safety Switch problem? We are experts with respect to RCD Fault Finding. If you are constantly tripping breakers then it is time to look at the cause before you get into real strife.
A Step by Step Guide to Reset Your Safety Switch.
Follow these steps to determine what has caused your safety switch to trip.
This is only recommended if your have switching type circuit breakers in your switchboard. An older board with the white or black re-wirable or cartridge fuses should not be touched as they are generally unsafe to work on and may present a risk of electric shock from exposed live parts.
- Step 1
If you have tried to reset your safety switch and it turns off instantly then you will need to unplug EVERY appliance inside your home. The plug needs to be physically removed from the power point, not just turned off at the switch.
Try to reset your safety switch. If the switch resets and stays on this may indicate a faulty appliance. Plug all your appliances back in one by one until the offending appliance trips the safety switch again. This is the easiest way to isolate a faulty appliance.
A fridge or air conditioner may trip a safety switch when the compressor starts up on one occasion and may not on another. These faults can be frustrating and quite hard to isolate.
If the switch will not reset, leave all your appliances unplugged and proceed to step 2.
- Step 2
Turn off all your circuit breakers in the switchboard where the safety switch is located.
Turn on your safety switch. If it still will not reset you will need to call an electrician.
If it resets OK then proceed to step 3.
- Step 3
Turn on your circuit breakers one by one.
You should find that one will trip the safety switch when turned on.
Leave this circuit off and keep trying to reset the remaining circuit breakers. The circuit that causes the safety switch to trip will need to be checked by an electrician.
This method may restore at least some of the power to your home whilst you wait for an electrician and could avoid an expensive call out on a weekend or after hours.
It is advisable to call an electrician to inspect any part of your electrical installation that you may suspect is causing faults with your safety switch.
Electrical & Security specialise in providing a wide range of services.
Thank you for the prompt service we received for our air-conditioner repairs. We searched for an Adelaide Electrician and you were the only company to return our call and the service was excellent. Thank you.
Thanks so much for wiring my office with the right fibre to take advantage of our internet speed. Was great. You were in an out and no one even knew you were there.
You are amazing. Our electrical engineers on site love when you come to assist on fault finding. We know we can always rely on you to work well with our team and get the solution we all need. It also helps that you get here in record time when things go pear shaped. I really appreciate your services.
Thank you so much for coming out in the pouring rain to fix our reverse cycle. It was so miserable I almost regretted calling you but your boys were fantastic and didn't complain once despite the cold. It was also very nice that they were able to fix things so quickly. Thank you so much.
We have been using you guys for years to provide alarm monitoring service and you have been fantastic. I appreciate your call out time and I know we are in good hands.
It took me ages to try to understand what I thought I needed and it took you 2 hours to walk me through and explain what would suit my needs AND my house best. I trust you guys and appreciate all you have done.